Rated thermal power: 14-116MW
Rated working pressure: 1.25-1.6Mpa
Fuel type: anthracite coal, meagre coal, lignitous coal, bituminous coal.
This boiler is a large industrial bulk boiler that uses coal as fuel, and is widely used in chemical factories, feed factories, paper factories, industrial and mining enterprises and central heating areas. Due to limitations for volume and transportation, we will disassemble the boiler and send parts individually. We can then send technicians if needed to provide on-site installation and debugging services for the customer.
|Type||Water supply( MW )||Water outlet pressure ( Mpa )||Water outlet temperature (℃)||Return water temperature(℃)||Air pre-heater temperature(℃)||Boiler volume( m3 )||Thermal efficiency( % )||Dimension after installation( m )|
|14||1.25||130||70||148||14.1||＞ 80||14.5 × 8.4 × 13|
|29||1.25/1.6||130/150||70/90||153||28.1||＞ 80||15 × 10 × 15.5|
|29||1.25/1.6||130/150||70/90||150||45||＞ 80||14 × 8.2 × 9.5|
|46||1.25||130||70||/||65||＞ 80||15.1 × 11.4 × 17.2|
|58||1.25/1.6||130/150||70/90||151||48||＞ 80||15.1 × 11.4 × 17.2|
|64||1.25/1.6||130/150||70/90||160||45||＞ 80||15.5 × 13 × 20|
The hot water boiler features complex processing links, and utilizes fine processing, which is an important factor in final product quality and safe usage by the customer.
1. Boiler material: seamless steel pipe
2. Welding process: Argon arc welding and radiographic testing
3. Bending shaping: The tube is shaped after the bending process in the pipe bending machine in order to ensure the coil outline dimension accuracy and ensure it meets GB/T17410 standards.
4. Water pressure testing: After shaping, the water pressure test for the tube is carried out before the boiler leaves the factory.
The industrial boiler is a natural circulation boiler that is divided into 2 parts. The upper area is the boiler heated surface, with the lower part consisting of the grate. The end of the boiler is equipped with an economizer and air-preheating system. The boiler also features a water circulation system, flue gas system, ash system and blowing system.
1. Boiler heated surface
The boiler heated surface consists of the steam drum, water drum, header, water wall and convection tube bundle. The water drum is also outfitted with a sewage device.
The boiler uses a chain grate with wind blowing from the bottom. There are 6 independent wind chambers in the grate, which can be adjusted based on user combustion conditions in order to save electricity.
The economizer is placed on the tail end of the boiler, and is used to recover residual heat from the flue gas. When the temperature of the exhaust gas is too high, the economizer will reduce the temperature and save fuel.
4. Air per-heater
The air pre-heater can heat the air before it enters the boiler, and thus, improve the boiler’s combustion efficiency.
5. Water circulation system
Water source—pump—economizer—drum—downcomer-- water drum-- riser tube-- steam drum-- steam outlet
6. Ash system
After fuel burning, the resulting ash will be discharged using a slag extractor at the end of the grate. Ash that isn’t quickly discharged will fall into the front ash bucket with the chain grate running. This means users do need to regularly clean the grate.
industrial boiler, coal fired boiler, coal furnace