Rated steam output: 2-6t/h
Rated working pressure: 0.7-2.5Mpa
Fuel type: anthracite coal, meagre coal, lignitous coal, bituminous coal, etc.
The horizontal coal fired steam boiler is an industrial package boiler that is designed to be directly hoisted to the customer’s site for easy installation.
The boiler is fueled by coal, and changes steam into water in order to heat water through the use of a heat exchanger. It provides heat for steam powered manufacturing equipment or general heating. It can provide heat for manufacturing equipment or as generalized heating in large structures.
The steam boiler is widely used in industry, and its main applications include:
|Type||Rated steam output (t/h)||Rated working pressure (Mpa)||Rated steam temperature (℃)||Boiler volume (m3)||Design thermal efficiency (%)||Maximum dimension of shipping part (m)
||Maximum weight of shipping part(t)||Overall size after installation (m)|
|2||1.25||20||4.3||＞ 77||7.4 × 2.6 × 3.5||28
|4||1.25||20||5.5||＞ 78||7.5 × 2.6 × 3.5||30||7.5×3.4×4.6|
|6||1.25||20||7.5||＞ 78||8.5 × 3.2 × 3.65||57.5||8.5×4×4.8|
The steam boiler has complex processing links, and the fine processing is an important factor of product quality and safety during use.
1. Boiler material: seamless steel pipe
2. Welding process: Argon arc welding and radiographic testing will be used.
3. Bending shaping: the tube is shaped after bending in pipe bending machine to ensure the accuracy of coil’s outline dimension satisfies GB/T17410 standard.
4. Water pressure testing: After shaping of tube coil, the water pressure test of boiler tube is carried out before leaving the factory.
The industrial boiler is a natural circulation boiler which is divided into two parts. The upper part is a boiler heated surface, and under part is a grate. The economizer and air per-heater are set at the tail of the boiler. The boiler features a water circulation system, flue gas system, ash system and blowing system.
1. Boiler heated surface
The boiler heated surface consists of a steam drum, water drum, header, water wall and convection tube bundle. Water drum is equipped with sewage device.
The boiler uses chain grate and wind blows from the bottom. There are 6 independent wind chambers under the grate, which can be adjusted according to the user combustion conditions to save electricity.
The economizer is placed at the tail of boiler, which is used to recover the residual heat of flue gas. When the temperature of exhaust gas is too high, the economizer can reduce the temperature and can save fuel.
4. Air per-heater
The air pre-heater can heat the air before entering the boiler and improve combustion efficiency.
5. Water circulation system
Water source—pump—economizer—drum—downcomer-- water drum-- riser tube-- steam drum-- steam outlet
6. Ash system
The fuel ash after burning is discharged by the slag extractor at the end of grate, ash not timely discharged will fall into front ash bucket with chain grate running. So users need to clean regularly.
industrial boiler, steam boiler, coal furnace, coal fired boiler